HVAC - (10) 20-ton Liebert HVAC units with rooftop condenser units provide cooling for data center floor - (2) 12-ton Carrier HVAC Units in UPS room
Fire Systems - Fire Suppression System consists of under raised floor Co2 system smoke detectors below raised floor, on, and above ceiling
UPS Systems - (3) UPS Units providing "A&B Power" - (1) Mitsubishi UPS Unit -300kVA (9800A Series) - Mitsubishi UPS unit has wet-cell battery plant -45 batteries total (comprises one string) - (1) Schneider Electric UPS Unit -160kVA (Galaxy VM Series) - (1) Modular Battery Cabinet - (1) Schneider Electric UPS Unit -225kVA (Galaxy VM Series) - (1) Modular Battery Cabinet
Generator Systems - (3) Caterpillar Diesel Generators "A+B" for UPS Units - (2) 800kW Generators - (1) 574 kW Generator - (2) diesel "day tanks" feed back to the main building diesel storage fuel tank, which is 5,000 gallons - (12) ASCO Automatic Transfer Switches
Security - Card Reader Access System (CCURE Software House) -(8) card readers total entrance into actual data center requires HID card swipe and unique pin code for access - (8) cameras installed with local DVR unit -remote monitoring and recording capabilities (4) IP cameras tied into separate software with recording and 24/7 monitoring capabilities - 24/7 lobby security (customers need to be on access list to get to 3rdfloor after hours, weekends, and holidays)
Cogent Toronto Pricing/Quotes
If you are interested in receiving a quote for Cogent Communications, Inc., please try our free quote service.