General data . 600 m² building . 1 Plant, 2 of technical facilities and IDC and 2 for personnel . Data center of 2 rooms of 100m² . Multi-operator physical connectivity with redundant connections and independent fiber rings . IDC construction with 60 mm concrete walls . Distribution of fully sectored facilities . Year of construction 2018 Infrastructures . 2 IDC Rooms of 100 m² . 1 Technical room for electrical installations and UPS . 1 Technical room for fire extinguishing installations . 1 Technical Room for air conditioning and generator sets . Independent air conditioning in each room . Rooms with technical floor . Floor strength of 2000 kg / m² . Floor raised 320 mm . Ceiling height from 316 to 330 cm Energy systems . Independent electrical connection from the transformation center of the supplying company. . Own space reserved for the installation of a medium voltage transformer. . Electrical room for the installation of the general electrical panels of the building (CGDBT), UPS and automatic switchboard. . Electric monitored room (CCTV), energy controlled with analyzers and refrigerated . Installation of 2 UPS units of 20 Kva in redundant parallel system, each one with its battery cabinet and isolation transformer to create its own neutral regime. Autonomy for batteries of approximately 45 minutes. . Two generator sets of 1000 Kva in redundant parallel with external diesel tanks of 1000 liters each. . Automatic switchboard RED-GRUP-RED
CPD TWN Jaen Pricing/Quotes
If you are interested in receiving a quote for Tower Net Infraestructuras SL, please try our free quote service.