The Maidenhead facility has been specified to the UK Data Centre Uptime Institute and EU Code on Conduct specifications for Tier 2 resiliency.
Power The site is supported by multiple diversely supplied 2 MW on site substation. This is distributed to n+1 PowerWave UPS systems for critical load. The UPS's are protected by multiple AKSA generators with 30 hours of fuel storage at full load onsite. There is a guaranteed contract to provide fuel every 24 hours by a local contractor to maintain 30 hours of fuel capacity. Each rack can be dual fed, up to 16 Amps capacity.
Cooling Cooling is provided by Airedale CRAC Water refrigerant cooling solution in each Data Centre hall configured to the N+1 standard per Data Centre hall.
Maidenhead Tier 2 710 rack capacity Single 16Amp
Diversely supplied 2 x 2 MW on site substations. N+1 PowerWave UPS systems for critical load. Multiple Generator configuration. Rack configurations from 1 to 16 Amp capacity. Blended Airedale CRAC Water Chilled/Condensing units in each data centre hall, configured to the N+1 standard per data centre hall.
Pulsant Maidenhead Pricing/Quotes
If you are interested in receiving a quote for Pulsant Ltd, please try our free quote service.